IEC Edition INTERNATIONAL. STANDARD. Surge arresters –. Part 5: Selection and application recommendations. INTERNATIONAL. IEC is not a mandatory standard but provides information, guidance, and recommendations for the selection and application of. 5. Voltages limited by arresters. Arrester power frequency witstand voltage. Resulting . An allowance of at least 5% (IEC ) is recommended. With this.
|Published (Last):||22 August 2007|
|PDF File Size:||3.95 Mb|
|ePub File Size:||9.25 Mb|
|Price:||Free* [*Free Regsitration Required]|
IEC System of Conformity Assessment Schemes
Our prices are in Swiss francs CHF. The user of surge arresters will, in that case, not be required to apply the whole process introduced here to any new installation and the selection of characteristics resulting irc prior practice may be continued.
Surge arresters – Part 5: Please note that the selected standard is invalid. Typical maximum eic voltages are given in Annex F. The Redline version is not an official document, it is available in English only and provides you with a quick and easy way to compare all the changes between the official IEC Standard and its previous edition.
Do 600999 need a multi-user copy? We accept all major credit cards American Express, Mastercard and VisaPayPal and bank transfers as form of payment.
IEC Standard – Home
It is likely, however, that for some systems, or in some countries, the requirements on system reliability and design are sufficiently uniform, so that the recommendations of the present standard may lead to the definition of narrow ranges of arresters. Selection and application recommendations Status: Fuses and other overcurrent protection devices Substations, surge arresters. It applies to gapless metal-oxide surge arresters as defined in IECto surge arresters containing both series and parallel gapped structure — rated 52 kV and less as defined in IEC and metal-oxide surge arresters with external series gap for overhead transmission and distribution lines EGLA as defined in IEC This edition constitutes a technical revision.
Related publications IEC Surge arrester residual voltage is a major parameter to which most users have paid a lot of attention to when selecting the type and rating. Subscribe on standards with our subscription service.
IEC | IEC Webstore
Valid Buy this standard. Selection and application recommendations Article no: This third edition cancels and replaces the second edition published in When you use our service you can be assured the ice editions and easy access.
Annexes H and I present comparisons and calculations between old line discharge classification and new charge classification.
TC 37 – Surge arresters rss. Shopping cart Close cart 0, foreach: Message to your colleague.
SS Valve type surge arresters – Terminology. This edition includes the following significant technical changes with respect to the previous edition regarding the new surge arrester classification introduced in IEC Sustainable Development Goals and standardisation, how do they connect?
Subscribe on standards – Read more. The following test ief forms are related: The standard is now in your shopping cart. Read more about SIS Subscriptions.
Surge protective devices connected to telecommunications and signalling networks – Performance requirements and testing methods. Contact us svenska Login. Selection and application recommendations. What is a standard?