Description: This users manual for Altistart 46 soft start motor controllers contains installation, setup, operation, and maintenance instructions. User’s manual ATS46, 9/21/18, English, Spanish, French, pdf MB. Data Bulletin. Cross Reference Guide for ALTISTART® 46 Soft Start Motor. User’s manual UNI-TELWAY ATS VW3G, 12/13/17, English, pdf MB. Programming manual ATS VW3G, 12/13/17, English.
|Genre:||Health and Food|
|Published (Last):||9 August 2012|
|PDF File Size:||2.66 Mb|
|ePub File Size:||16.90 Mb|
|Price:||Free* [*Free Regsitration Required]|
J7 Connector if pump unit J9 J10 J11 Conversion instructions for sizes 4 and 5 6 – Loosen the fixing screws of the metal support. manula
It requires a fair knowledge of the product and its applications ventilation, pumping, convoying, …. The time of delivery of the repaired or new element will be given by the dealer or the agency.
Value kept for the test voltage 2 V AC Seco nd ar y: Assembly size 2 Parts altisyart Part 3: Only the connection lead between the Altisart 46 receptacles and the point sub-d receptacle is different.
Care should be taken to ensure that this card is positioned correctly, placing the connectors towards the top of the unit. The motor does not brake the load correctly The motor does not brake the load correctly cause check remedy High inertia After the brake request, there is current into the motor even in a discontinuous way.
The pump transformer must be removed.
Altistart 46 Soft Starters – Documents and Downloads | Schneider Electric
For more information, please contact S. The product structure is identical to the one of ATS23, that is to say, a control element common to all sizes, and a power element specially designed to each calibre.
Core housing Material U. SY3KC Blue wire mark 3: No wire out of the transformer lower part 2 mm minimum mandatory Outlet order is not important. Starter not supplied with current on L1-L2-L3. Outlet order is not important White wire mark 1: PiF Phase inversion Fault Measurement principle: Conversion instructions for sizes 4 and 5 Remove the cable from the current transformers by cutting the clamps and unscrewing the connection screws on the transformers.
The following instructions have to be performed: Under Load Level release threshold Function Under load detection Under load fault is generated only in permanent rate. SY3CM 18 5 point socked marked J5: USF power supply fault, when start mode is required Up to now experience: The time taken to perform the conversion is approximately two hours, to which site transfer time must be added. Connectors Thyristors Connectors Filter card Disconnect the filter cards do not remove them from the busbars.
Measurement alhistart Screws Brackets 7 – Remove the fan cover two screws with a 7 mm spanner. DZ4DP 16 2 Black wires marks 16 and Lower the support to connect the 4 or 8 wires to the connector in accordance with the diagram. The starter software version can be seen through a window after additional part disconnection. Care should be taken not to pinch the wires when reassembling this part. Assembly size 3 Parts list Interconnection drawing Part 4: They are constantly monitored to guarantee a high quality level.
SBS – Hands on experience.
Altistart 46 Maintenance Manual
Humidity mankal according to IEC and 3. For floppy disc 2, follow the instructions that will appear on the PC screen. Outlet order is not important. EtF External Fault Measurement principle: If the motor runs on RUN order and stops at the 3 stop configurations, without disable, the repair is over.
White Green Blue Red diagram of the customer terminal block 12 – Remove the four screws attaching manua transformer no. Use the fixing points to run the cables along the insulating dividers and connect up to the clips. Attach the assembly with plastic clamps in the appropriate locations.
Altistart-« 46 Soft Start Motor Controllers Users Manual
Assembly size 5 Parts list Part 6: Reference Rated ef f. The starter supplies current but the motor does not run. If, for practical reasons, you do not want to disconnect the protection and control circuits, top to bottom terminal resistance can be measured. Starter disrupted by a DC converter 1.
If the conditions are dif ferent, algistart have to be specified in chapter 7: SY3KC Red wire mark 4: Their value is calculated to obtain rated current of each coiling for primar y rated voltage.
Connect the cables to the plug-in units according to the following drawing.